This UL Listed, ANSI C12.1 and C12.20 certified kWh meter can be used on nearly any electrical system in common use and can also count pulses from up to 3 pulse-output devices, as well as control up to 2 external relays. This meter also meets California's Title 24 requirements for service metering. Free cloud data service when paired with an EKM Push gateway!
System: Single-Phase, 3-Ph. 3-Wire, or 3-Ph. 4-wire
Data: Smart Meter v.4 RS-485 Communications
Certifications: California Type Approval, ANSI C12.1 and C12.20, UL and cUL Listed
Warranty: 10 year warranty
Model: EKM-Omnimeter Pulse UL v.4
EKM-OmniMeter Pulse UL v.4 -- Our most advanced universal smart meter to date, now with the ability to count pulses from up to 3 pulse-output devices, and control 2 external relays. This model is certified to meet (it actually exceeds) ANSI C12.1 and C12.20 standards. It is also UL and cUL Listed. This is truly the one meter to meet all of your metering needs!
This meter has been designed to meet California's 2013 Title 24 (page 151) requirements for energy management and service metering (Section 130.5A). Depending on the service, these requirements can include – Instantaneous kW demand, resettable kWh, historical peak demand, and kWh per rate period; all of which are provided by this meter.
The Omnimeter Pulse UL v.4 can count the pulses from up to 3 different pulse output devices, as is explained in this video. These could be pulses from our Pulse Output Water and Gas Meters or from any other un-powered dry contact pulse output device. Pulse Input ratios can be set in software from 1 to 9999 pulses per increment (the default ratio is now 1:1). The real-time state of the 3 Inputs can also be polled in EKM Dash software, the Omnimeter Pulse UL v.4 will return a High or Low state for each pin in real-time (use this for sensing switch states, open or closed doors, etc).
The Omnimeter Pulse UL v.4 comes with 2 controllable relay outputs. These can be controlled via RS-485, either locally or over the internet from anywhere in the world using the EKM Dash. You can set the outputs to be high or low to drive an external relay. The Relay Control Outputs both provide up to 50 mA at 12 volts DC. Control the EKM-Switch120 directly, or control lights, motors, entire buildings, implement Demand Response, Load Shedding, etc. via relay control. The Relay Control Outputs can also be set to go ON or OFF from 1 to 9999 seconds. The real-time state of the outputs can also be polled via RS485. The outputs can also be used to power an external device (Wireless 485Bee Module, sensors, etc). Please note that the relays cannot be controlled when reading the meter with the current version of the EKM Push system (Push2). You will need to be reading the meter with an EKM Blink USB Converter, iSerial, or wait for the next version of the EKM Push system (Push3).
The Omnimeter Pulse UL is also a revenue-grade universal kWh meter. It can meter systems ranging from single-phase 120V 2-wire, single-phase 120/240V 3-wire, 3-phase 3-wire 120 to 240 volts, or 3-phase 4-wire 120 to 240V. 50/60Hz. It Supports CTs from 100A to 5000A. This meter will work with any system that is commonly used in the world. Accurate to 0.5% (Class 0.5)
The Omnimeter Pulse is also great option for solar Net Metering. In addition to Total and Reverse kWh, that all of our Omnimeter models provide, these meters also provide the direction of current in real time. This makes it possible to know, in real time, if you are generating more power than you are consuming, and whether you are sending or pulling power, to or from the grid. This meter is listed by the California Solar Initiative as eligible for Performance Based Incentives (PBI). In other words, you may be eligible to earn money back from your Utility, in California, by using one these meters to monitor the performance of your solar array. Check with your local Utility to see if you are eligible. Also, because it is certified to ANSI standards, it is possible to receive SRECs (Solar Renewable Energy Certificates) with this meter.
This meter uses our full range of compact Current Transformers (it cannot meter electricity with out at least one). The CT ratio can be set internally to work with up to 5000 amp CTs (no multiplier needed).
Use 1 CT for 120 volt single phase North American, or 230 volt 2-wire foreign systems
These meters are also supported by our revolutionary EKM Push system. This is our cloud-based, plug-and-play, meter data solution. We are really excited about this new system, and recommend it for most remote reading applications that use our Omnimeter models. EKM Push users can also take advantage of Encompass.io, which is our free online dashboard and meter management suite.
Encompass.io is our free online meter management platform for monitoring and managing meters. It is designed specifically for people who are remotely reading their meters via the EKM Push system. This platform can be used to visualize usage on dashboards, visualize cost, monitor trends, group meters, and a lot more. Each meter in Encompass can also be set up to email you PDF and CSV reports that you can use to monitor you meters and/or use for billing. Here is a sample PDF report:
The EKM Widget offers another option for quickly seeing your meter data online for EKM Push users. It is also easy to save and share your Widget setting once you have it setup how you want. Here is an example:
Our Omnimeters are also fully supported by our free, remote reading, EKM Dash software. If you want to read your Omnimeter on a computer locally, without the EKM Push system, then this software is what you would use. You will also need an EKM Blink USB Converter in order to do so.
For more information about our products and services, we encourage you to visit our online Knowledge Base, which provides spec sheets, videos, tutorials, FAQs, diagrams, and more.
I purchased a V4 meter to measure power of a split phase 120/240V. My house has an energy storage system installed so I can flow power back to grid. I notice that the total RMS_Watts_Tot is always a sum of RMS_Watts_Ln_1 and RMS_Watts_Ln_2 regardless of current direction State_Watts_Dir (1,4 or 7). How do we use EKM info to determine the total power watt direction for split phase120V/240V?
If you have an Omnimeter Pulse v.4 and you use the EKM Dash software or the EKM Push system, the Net Watts on each line and Total Net Watts are already provided for you. If you want to use your own software, you can calculate Net Watts on your own. We calculate Net Watts on each line and Total Net Watts from the data provided by the Omnimeter Pulse v.4. Net Watts on each line is calculated by taking the Watts on each line and applying the direction of current to that line. The direction of current bitmap is on page 2 here: http://documents.ekmmetering.com/Omnimeter-Pulse-v4-Parsing.pdf Calculating the Total Net Watts would use this formula: Total Net Watts = Net Watts Line 1 + Net Watts Line 2 + Net Watts Line 3
I have two 220V loads and I want measure total kWh across both. Is that possible with this unit (v.4)? If possible, how would the wiring/CTs be arranged?
If both loads use the same phases (same voltages) then it is possible to meter both with one meter. You can do this by installing CTs on the wires going to each load an then running the CT leads to the same ports on the meter, for each phase. Or you can pass multiple wires through the CTs, provided that all of the wires going through each CT are on the same phase. In these cases the amperage is aggregated to give you a single total for both loads.
I have approximately 5 separate loads off the same Electrical Service that I would like to track metering on do you have a single meter that will work??
Our v.4 Omnimeters can meter up to three separate loads up to 120V. This meter provides a cumulative Total kWh as well as kWh on each line separately. If the loads you're trying to meter are 110v or 120v then you could meter the 5 loads with two of these meters. You would also need one current transformer per load, or up to three per Omnimeter.
Hi there, I noticed that the UL listed meters come with a 10yr warranty. They do not seem to be compatible with European voltages however - eg 240Vac phase to neutral, or 415Vac phase to phase. Is there a meter that I can purchase with a 10 yr warranty that is also compatible with the higher voltages???
We don't currently have a UL Listed meter that is certified for voltages above 240V. We are currently working on a new meter model that will be able to handle up to 600V systems and our aspiration is to have it UL Listed up to at least 480V. This meter will also have a 10 year warranty. We don't have a definitive timeline for this meter but are hopeful that it will be available some time in mid 2017. If you would like us to let you know when it is available, please contact us at email@example.com.
I'm looking for a device that can recorded KwH for different time periods, such as on and off peak times. Can this unit do this?
All of our Omnimeter models have Time Of Use (TOU) capability. You can set the TOU periods for up to four tariff periods. This will give you separate kWh values for each time period you set up. To set the TOU periods you need to be reading the meter directly with a USB Converter and our EKM Dash software.
Once the TOU settings are made then you can read the meter(s) with our EKM Push system if you wish.
I've got a EKM Omnimeter Pulse UL v.4 connected to a stainless steel pulse output water meter and an external 110v relay. I'd like to turn on a relay (controls a pump) after a specified number of pulses for say 10 seconds. I can figure out how to count pulses, and I can figure out how to turn on/off a relay from DASH for s specified period of time, but I can not see how to have the pulse count trigger the relay.
At this point EKM Dash isn't capable of triggering a relay. Triggers can only send an email based on a defined parameter. However, we are planning to add triggered relay control at some point relatively soon. Stay tuned.