Description: Universal Smart Meter
Voltage: 120 volts, 120/240 volts, 120/208 volts, 230 volts, 277 volts, 480 volts
Amperage: Up to 5000 amps
Type: External CT, 50 or 60 Hz
System: Single-Phase, 3-Ph. 3-Wire, or 3-Ph. 4-wire
Data: Smart Meter v.3 RS-485 Communications
Model: EKM-Omnimeter I v.3
This meter is truly a worldwide universal meter and can be used to meter a wide variety of electrical systems. It meters systems from 120V single-phase 2-wire, to 480V 3-phase 4-wire, both 60Hz and 50Hz. There is not an electrical system, up to 480 volts, in common use that this meter will not support. Accurate to 0.5% (Class 0.5). We now stock CTs for up to 5000A.
Note: this meter requires Current Transformers. The CT ratio can be set internally in the meter to work with up to 5000 amp CTs (no multiplier needed).
- Use 1 CT for 120 volt single phase North American, or 230 volt 2-wire foreign systems
- Use 2 CTs for 120/240 volt single phase systems
- Use 2 CTs for 3-phase 3-wire systems (no neutral)
- Use 3 CTs for 3-phase 4-wire systems
These meters are also supported by our revolutionary EKM Push system. This is our cloud-based, plug-and-play, meter data solution. We are really excited about this new system, and recommend it for most remote reading applications that use our Omnimeter models. EKM Push users can also take advantage of Encompass, which is our free online dashboard and meter management suite.
Our Omnimeters are also fully supported by our free, remote reading, EKM Dash software.
For more information about our products and services, we encourage you to visit our online Knowledge Base, which provides spec sheets, videos, tutorials, FAQs, diagrams, and more.
Easy clip-on DIN rail mounting.
This meter has been accuracy tested and certified for by the State of California Department of Weights and Measures. It is California Type Approved and meets California standards for revenue grade metering. Many other states accept California Type Approval for their metering requirements.
How to install an Omnimeter (it is a v.4 Omnimeter in this case but v.3 Omnimeters are installed in a similar way):
Use the Omnimeter in conjunction with an EKM Push gateway to provide rich, real-time and historical data. The Widgets below provide one way to visualize your meter data in real-time, as well as your usage history. More info here: EKM Widget
Omnimeter I v.3 without terminal block covers:
Spec Sheet: EKM-Omnimeter Spec Sheet
To better understand the differences between Omnimeter models you can download our Omnimeter and Communication Device Comparison Chart.
- Additional Information
- Questions and Answers
Questions & AnswersExpand allCollapse allSort byMost Recent QuestionsQ:Does the monitoring option direct-link between the OmniMeter I v.3 and lets say a router? i e, can I split out a CAT5 and directly connect to my Omni for monitoring?1 answersQ:Is the meter output BACnet compatible so that it can be read by our building management system?1 answersQ:Does the digital display read amperage as well on each leg separately ?1 answersQ:Can you stop the Omnimeter I v.3 from auto cycle mode to just read Total kWh?1 answersQ:Will the Omnimeter fit inside a typical loadcentre that is sized for standard MCB's?1 answersQ:Is there a simple way to zero the total every month, for submetering uses?1 answersQ:Is there a way to prevent tampering? If someone removed a CT, would the meter become ineffective?1 answersQ:1- Is the spit core current transformer as accurate as the solid core CT? 2- Can I assume that the split core CT is easier to install and a bit safer to install? 3- Which models record data?0 answersQ:Can I put multiple loads of the same phase through the CT for a cumulative measurement? I need to monitor multiple loads but individual totals is irrelevant, need the total of all. I need to monitor 10 different loads.1 answersQ:We want to find the meter reading in two different places in the building. Can we connect another digital display for each meter? We have 120 meter in the building.1 answersQ:I need to monitor the output of a DC power supply, both wattage output and accumulated KWh usage. Can i connect the output of the DC supply through the meter to accomplish this?1 answersQ:Can I use multiple sets of CT's to monitor three different 3 phase breakers?1 answersQ:Does this item include 1 or 2 CTs? Or do I buy them separate, and do you sell them?1 answersQ:The Omnimeter I v.3 apparently displays 15 different data values. I only want the total KWH. Is it possible to set the meter so that this is all that it displays or do I have to wait 75 secs until it comes round again?1 answersQ:Can I use this to monitor my total electric usage? My local power company installed a new "smart meter" and my light be has doubled!1 answersQ:Is there a wire length limitation between CT's and meter?1 answersQ:Does the meter scroll through the display readings (i.e. volts, amps, PF, kWh, etc.) in 5-second time intervals?1 answersQ:WIll these meters work on 230vac, 1-phase, 2-wire-230 to ground?1 answersQ:Is this one 3 Phase available?1 answersQ:Does this meter record the use of electricity so I can deduct from the electric bill?
- Installer Directory
Customer Reviews 6 item(s)
- Easy to install, great remote metering solution for renters.
I've just installed my first meter in a rental unit. I'm extremely happy with how it has functioned so far. It gives me everything I need to bill my tenant and to allow them to monitor their own usage on a daily basis. The EKM Push product also has an excellent interface with the new encompass.io beta. Great price, super interface, easy to install. My only con was not selecting the right core size for my electrical line initially, and when I did, I had to skin the line for the core to fit. Since I have an upstream shutoff for the line it was no problem. The split core makes shutting the electricity off less crucial but size is very important. Make sure to measure your line size first before ordering as your sheathing may be larger or smaller than the expected wire diameter. Keep up the great work!
Value Quality Price
- Excellent meter for lab use
I now have installed about 15 of these meters for UL and CSA electrical testing in labs in 120V, 240V and 460 volt circuits . I have written vb.net and labview code for data collection and designed a pic lcd interface to view the data directly off the meter. Calibration is right on the money and have had no out of tolerance meters so far. To increase the accuracy below 5 amps I would suggest using 10 turns through the coil and doing the math accordingly.
Price Value Quality
- Fit the need perfectly
The Omni I v.3 fits the need perfectly. I'm using three (3) of them to submeter the output of three (3) small (5kW) wind turbines. The turbines connect to one utility metering point. Not only can I obtain the total turbine to utility grid output, but I can also monitor each turbine's output. The turbines are in close proximity to each other. If one has a lower output, this may be an indication of need for maintenance before the self-diagnosis of the turbine controller indicates maintenance. Very easy to connect to the turbine controllers. Customer extremely pleased with performance. The utility's digital smart meter was not properly programmed initially. After installing the Omni I v.3 and comparing the readings, the utility re-programmed their meter and all is well.
Price Value Quality
- Compact, simple to install
I just installed my first EKM-OmniMeter I v.3. I expect to install 1, possibly 2 more in the coming months. I used the standard shipping and received the unit in 2 days I think, not more than 3 for sure. It was well packaged and arrived safely.
Having had experience in the past with "multi function" gadgets I was concerned that installation would be bewildering. What I found was very clear and concise, step by step instructions which made it easy to install. (It worked right the first time I turned on the power).
The compact size allowed me to install it inside of my main breaker panel. I used a nibbler to make a window in the breaker cover so that only the display is visible whenever I open the panel door. Very nice!
Wish list: I didn't know I needed the 1 amp fuse holders - it would have been nice have this item listed as a necessary accessory. It would also be nice if there were a way to select which information is displayed. It's very cool to see the power factor (whatever that is) and other information but all I really care about is the KWH. I'd like to be able to open the cover, look at the reading and be on my merry way.
Regardless of the foregoing, I think this is a very good product. The bottom line is that it's going to add money to my bottom line.
Price Value Quality
Wrks as expected!
Price Value Quality
- A great product
This meter, used with EKM's CTs, iSerial, and Reader software has allowed me to sub meter my rental units and bill my tenants based on their usage. I have also begun to see my energy bills decrease now that my tenants are paying for their own power. Overall, Im very happy with it.
Price Value Quality
You may also be interested in the following product(s)